Standards as High as Your Own
NECA Online Help Desk Please leave a message
Re: CQD answer published Thursday, December 22, 2016 -Article 250 Tables
Something that may help David Cotter understand which table is appropriate to use is for him to understand that Tables 250.66 and 250.102(C)(1) are applicable where there isn't an overcurrent protective device immediately ahead of the ungrounded conductors, such as at services and separately derived systems. Table 250.122 will always be used where there is an overcurrent protective device as part of the circuit, such as with feeders and branch circuits. This is why Tables 250.66 and 250.102(C)(1) are based on the ungrounded wire size and Table 250.122 is based on the fuse or circuit breaker used on the ungrounded conductors.
The only difference between conductor sizes between Tables 250.66 and Table 250.102(C)(1) is T250.66 has definitive maximum conductor sizes for grounding electrode conductors for corresponding ungrounded wire sizes >1100 kcmil CU and >1750 kcmil AL. This is because there is a limited amount of current that will flow on the grounding electrode conductors during a fault, and the wire sizes indicated have been proven to be of sufficient size to handle the current imposed on the grounding electrode system without damage to the grounding electrode conductor. Table 250.102(C)(1), on the other hand, requires the grounded conductor, main bonding jumper, etc. [see list at top of T250.102(C)(1)] to be sized at 12.5% of the ungrounded conductors when the equivalent ungrounded conductor size exceeds 1100 kcmil CU and 1750 kcmil AL.
Before the 2014 NEC, the only tables we had to work with were T250.66 and T250.122. The rules didn't change in the 2014 edition. T250.66 was broken out into two separate tables for clarification purposes.
Thanks, Eddie Guidry
Hey Eddie thanks for your comment. Your description provided much more clarification.
Thank you for the comment! Your comment must be approved first
You've already submitted a review for this item
Thank you! Your review has been submitted successfully
Login to be able to comment
Comment cannot be empty
Rating is required
You typed the code incorrectly. Please try again
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: email@example.com.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.