Standards as High as Your Own
NECA Online Help Desk Please leave a message
Re: CQD answer published Wednesday, December 21, 2016 -Garage Outlets
Hello, In your answer to the Code Question of the Day that was published on Tuesday, December 20, 2016, you stated that it is permissible to install garage door openers on the same circuit as the garage receptacles. I respectfully disagree because the garage receptacles shall be in addition to those that are required for the garage door openers per Sec. 210.52(G).
Truly, Joseph A. Kraft
Hey Joseph thanks for your comment. Your are correct that the receptacle(s) must be in addition to the receptacle(s) installed for specific equipment as stated in 210.52(G) but it doesn't prohibit those receptacles from being supplied from the same branch circuit.
A change to the 2017 NEC in 210.52(G) requires at least one receptacle outlet to be installed in each vehicle bay and it cannot be more than 5 1/2 ft above the floor. Also new to the 2017 NEC is 210.11(C)(4) which requires at least one 20 ampere branch circuit be installed to supply receptacle outlets in garages. Other outlets (such as lighting) are not allowed as stated in the last sentence of that new subdivision.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: firstname.lastname@example.org.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.