Standards as High as Your Own
NECA Online Help Desk Please leave a message
Hi Charlie, my question has to do with access. In let’s say a multi-story hotel in the hard lid ceiling there is heating, motorized dampers, lighting controls or any number of other electrical appliances or devices with disconnect switches or not, is there anything in the NEC concerning proper access to service or replace items as motors, switches and the like, or is it all out of the building or mechanical codes? Obvious interest in the electrical service, repair and replace aspect with concerns for the professional who performs work on equipment. Thanks for your time. Butch
Hey Butch thanks for your question and your concern for workers that maintain and service equipment. All electrical equipment must have access and working space as stated in 110.26. If equipment is likely to require examination, adjustment, servicing, or maintenance while energized the dimensions in 110.26(A)(1), (A)(2), (A)(3), and (A)(4) must be provided. Motors must be located so adequate ventilation is provided and so they can be readily maintained as stated in 430.14. There are other rules such as 240.24 and 404.8 that require some equipment to be readily accessible as that term is defined in Article 100.
Thank you for the comment! Your comment must be approved first
You've already submitted a review for this item
Thank you! Your review has been submitted successfully
Login to be able to comment
Comment cannot be empty
Rating is required
You typed the code incorrectly. Please try again
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: email@example.com.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.