Standards as High as Your Own
NECA Online Help Desk Please leave a message
Re: CQD answer published Friday, March 10, 2017 -Barn Feeder
Charlie, in the question about the barn supplied by a feeder you said that two ground rods are needed unless the 25 ohm rule is met. Is that enough or are other electrodes required.
Thank you, Taylor
Hey Taylor thanks for your follow up question. Buildings and structures supplied by feeders must have a grounding electrode system that complies with Part III of Article 250 as stated in 250.32(A). Any and all of the grounding electrodes in 250.52(A)(1) through (A)(7) that exist must be bonded together and used as the grounding electrode system as stated in 250.50. If no grounding electrodes exist then one or more of the ones in 250.52(A)(4) through (A)(8) must be installed such as two ground rods or a single ground rod that meets the 25 ohm resistance value.
This article gives the light in which we can possibly notice the reality. This is very nice one and gives indepth information. Many thanks for this nice article. Obat Herbal Kanker Otak Stadium 4
Within a university thesis for research I must search sites with relevant information on given topic and give them to teacher our opinion and the article. Your article helped me a lot. Obat Kanker Otak Stadium 4 Mujarab
This really is my first time check out here. From the tons of comments on your articles, I guess I am not just one having all the enjoyment in this article! Obat Herbal Kanker Otak Stadium 4
I really enjoy simply reading most of your weblogs. Simply wanted to inform you that you have people like me who appreciate your work. Undoubtedly an excellent post. The information which you have provided is very helpful. Obat Herbal Kanker Usus Besar
Just keep publish what you are passionate about, and the visitors will visit your post. Obat Kanker Usus Alami
Very nice post. I just bookmark your website and want to says that I have truly enjoyed exploring your weblog posts. Cheers Obat Herbal Kanker Usus
I been very encouraged to locate this website. I desired to warm regards with this special study. I certainly savored every it and I've you bookmarked to look in fresh things you publish. Obat Herbal Kanker Hati Stadium 4
The globe will be transforming fast. people are also having altered.day by day time we are becoming more dependant on degital system.you're making me think of this really.You have a pleasant method of sharing your thoughts. Obat Kanker Hati Paling Ampuh
This is definitely really a brilliant publish, many thank you for telling Good luck I found out about this primary blog site. Obat Herbal Kanker Hati Tradisional
Hi I think you did not understand the exact values of the two rods which should be used for feeder. You must know that the electrodes should same of 25ohms each. For better clarity I ask you look into top writing service blog where you can get tutorial on this topic which will be very much helpful to you.
Thank you for the comment! Your comment must be approved first
You've already submitted a review for this item
Thank you! Your review has been submitted successfully
Login to be able to comment
Comment cannot be empty
Rating is required
You typed the code incorrectly. Please try again
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: email@example.com.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.