Standards as High as Your Own
NECA Online Help Desk Please leave a message
Re: CQD answer published Thursday, May 10, 2018 - Locking Equipment
In an emergency situation, ‘first responders’ such as firefighters may need to get access to a locked electrical room area or enclosure (as allowed per 110.26(F) , 110.31 & 490.35). Are there requirements or other guidance for enabling access for the first responders into those locked areas, if for example, the qualified persons with the access keys are not available at the time of the emergency.
In other words, the doors are being locked to keep unqualified persons out in normal circumstances, but in an emergency situation, we don’t want to excessively hamper access for the ‘first responders’. Is there any guidance on accommodating access for first responders to locked areas such as this?
Thanks, Chris Walker
Hey Chris thanks for your follow up question. Not really, at least not in the NEC. There are some rules in 645.10 and 690.12 that include wording about first responders but not rules that specifically prohibit locking doors or equipment enclosures. There are some provisions in other documents such as Fire Codes that authorize fire code officials to require key boxes under certain conditions.
There is an effort to add a rule for outdoor readily accessible emergency disconnecting means for one and two family dwelling units in the 2020 NEC. When the First Draft Report is available, scheduled posting date is July 6, 2018 you can look at the proposed change to add 230.85 based on First Revision No. 8462 and submit any comments you have at nfpa.org/ under the Next Edition Tab. Based on the definition of Accessible, Readily in Article 100 that disconnecting means could still be locked.
The concern you have is valid and has been asked by others. But some firefighters have suggested that locks on doors are not a problem - they have axes, power tools and other techniques to get through them!
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: firstname.lastname@example.org.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.