Standards as High as Your Own
NECA Online Help Desk Please leave a message
Seems many inspectors disagree on this code section: Permitted use of cords 400.10, 400.12. What is your opinion? Can a flexible rubber power cord provided as part of a condensate pump be allowed above a drop ceiling? Also, what about it use in a drop ceiling used for environmental air (aka: plenum)?
Thanks, Alan Chech
Hey Alan thanks for your question. The words "power supply cords" have been added to 400.12 of the 2017 NEC which makes it clear that they must comply with that section. So no, they are not allowed above suspended or dropped ceilings (whether it is used for environmental air or not) as stated in 400.12(5). Exception No 5 to 400.12(5) was added to allow them in other spaces used for environmental air if the flexible cord is in a metal enclosure or a nonmetallic enclosure specifically listed for use in an air handling space per 300.22(C)(3). It is not likely that the condensate pump cord will be in that type of enclosure.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: email@example.com.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.