Standards as High as Your Own
NECA Online Help Desk Please leave a message
Re: CQD answer published Monday, December 19, 2016 -Bathroom
Hi Charlie, regarding the panel in the basement bathroom where more than 6 feet away from any plumbing fixtures. If there were no walls or curtain dividers surrounding the fixtures, just in open view. Would a whole basement without any rooms be considered a Bathroom?
Hey Jerry thanks for your question but that image seems like a lack of privacy. The term "bathroom" is defined in Article 100 as an area with a basin and at least one other plumbing fixture. It is not limited to a room because in some locations such as in hotels the bathtub and toilet are in a separate "room" from the sink. Even though the basin is not in the same room as the other plumbing fixtures it is likely to be used in the same way regarding personal grooming appliances so requiring receptacle GFCI protection as stated in 210.8(B)(1) makes sense.
Looking at it from a different perspective as your question asks - how far the area that is considered a bathroom extends is not described. It is up to the AHJ to make the determination. I would not consider the entire basement a bathroom unless it was all used as a litter box.
Very well written admin and I love to read more info, so keep updating we will happy to visit again and again to your blog... Bes
Roland Garros en Direct
Thank you for the comment! Your comment must be approved first
You've already submitted a review for this item
Thank you! Your review has been submitted successfully
Login to be able to comment
Comment cannot be empty
Rating is required
You typed the code incorrectly. Please try again
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: email@example.com.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.