Standards as High as Your Own
NECA Online Help Desk Please leave a message
Hello, My name is Michael, I am an electrician in New Jersey. I just want to say thank you for all that you do for us out there in the field, I read these questions and answers with my crew every day, we are all very grateful.
My question is with regards to pool lighting installations. It is my understanding that any and all pool lights that are underwater should be terminated in a pool box. I have very little experience with pools, however, in this particular instance, I have 12 Low voltage lights in the pool all terminating in one central location with switch legs going back in to the house. The central location happens to be a retaining wall behind the pool that is approximately 4 feet above the water level. What I would like to do is pipe all of the lights into one large quazite box, and pipe everything underground back into the house. I just don't know if this is a violation.
Thanks again, Michael Nolan
Hey Michael thanks for your question and the compliment. Conduit connected junction boxes that extend to forming shells or mounting brackets of a no-niche luminaire must be listed, labeled, and identified as a swimming pool junction boxes as stated in 680.24(A)(1).
Swimming pool installations have a lot of unique rules and the risk of shock and electrocution increases due to the wet and corrosive environments usually present. Consider having someone experienced in pool installations work with you or mentor you until you gain that experience.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: firstname.lastname@example.org.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.