Standards as High as Your Own
NECA Online Help Desk Please leave a message
What is the correct way to bond the neutral in a residential main circuit breaker panel. I have always ran the ground wire to the street side of the water meter & jumpered across the meter & connected to the neutral bar. I have also seen the ground connected to the closest cold water pipe & the water meter jumpered .the code isn't very clear on this, which way is correct. Is it also necessary to jumper the hot & cold water piping at the water heater? Keep up the good work, thanks
Hey Jim thanks for your question and the kind words. The grounding electrode connection to a water pipe must generally be made with the first 5 feet of where the water pipe enters a building as stated in 250.68 (C)(1) but it is not limited to the street side of a water meter. A bonding jumper must be installed around any insulated joints and around any equipment likely to be disconnected as stated in 250.53(D) (1) and 250.68(B). Metal Water Piping Systems must be bonded as stated in 250.104(A). It does not specifically state that both the cold and hot water piping systems be bonded but each would likely be considered a separate piping system if they are not electrically connected together such as by the use of dielectric fittings at a water heater. Many plumbing fixtures are made of nonmetallic materials so usually do not provide continuity.
<a href="http://www.photoeditingindia.com/">photo clipping service</a>
Thank you for the comment! Your comment must be approved first
You've already submitted a review for this item
Thank you! Your review has been submitted successfully
Login to be able to comment
Comment cannot be empty
Rating is required
You typed the code incorrectly. Please try again
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: firstname.lastname@example.org.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.