Standards as High as Your Own
NECA Online Help Desk Please leave a message
Raceway Fill and Adjustment Factor Part 1.
I need to know how many #10 awg thhn wires and #18 awg dimming wires derated I can fit in a 1" conduit? How would you derate and split up the different wires to know how many we can have in each pipe.
Hey Michael thanks for your question(s). Depending on the type of conduit you are using the .22 section of the applicable Article references Chapter 9, Table 1 for the percentage of interior area of the conduit that can be used to determine the number of conductors allowed. For over 2 conductors it is limited to 40% as shown in Table 1. Note 5 to that table refers to Table 5 for conductor dimensions and Table 4 for the conduit dimensions. Using Rigid Metal Conduit (RMC Article 344) as an example find that table within Table 4 (the 9th one). The second column has the conduit trade sizes and the fourth column has the cross sectional area in square inches that can be used based on 40%. The fourth line is for 1 inch RMC and in the fourth column 0.355 square inches can be used to determine the number of conductors allowed. In Table 5, locate THHN in the first column then use the row with 10AWG size then go to the center column for the area in square inches for a single conductor which is 0.0211. You don't mention the insulation type for the 18 AWG conductors but for example if they are TFN, four lines up is their area which is 0.0055.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: email@example.com.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.