Standards as High as Your Own
NECA Online Help Desk Please leave a message
Subject: 680.12 2008 NEC
Would a maintenance disconnect be required for a self-contained pre-packaged spa with a GFCI and main breaker factory installed? Would this satisfy the requirements of 680.12? The disconnect is accessible from a screwed on panel located on front of spa skirt.
Town Of Wethersfield
NEC 680.12 requires that a maintenance disconnecting means be readily accessible and located within sight but not less than 5 ft. from the inside walls of the spa. This requirement is meant to prevent anyone from reaching the disconnect while in the spa.
NEC 680.41 requires an emergency shutoff switch for the purpose of stopping the spa pump motor. The emergency shutoff switch can be the maintenance disconnecting means required by 680.12 or a remote control circuit to open the pump circuit.
In either case the shutoff switch must be located not less than 5 ft. from the spa. The emergency cutoff switch is not required for single-family dwellings according to 680.41 but the maintenance switch is required by 680.12.
The disconnecting means for the spa you are referring to does not meet the requirements of being not less than 5 ft away from the spa. It is located behind the screwed on panel and can't be reached by someone in the spa but there is no exception to either 680.12 or 680.41.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: email@example.com.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.