Standards as High as Your Own
NECA Online Help Desk Please leave a message
Hi Charlie, thanks for keeping this great code forum going. My question is regarding transitioning from one wiring method to another. The common field practice is to use a combination of different fittings to achieve the transition. Is this a code violation, because these fittings need to be listed for the transition? Thanks, Tom Harwood.
Tom, your welcome and thank you for participating in the CQD. Using “Homemade” transition fittings creates several problems, the listing being one of them. The AHJ needs a basis on which to approve an installation. Section 300.10 requires electrical cables, raceways, boxes, and fittings to provide effective electrical continuity. When a “Homemade” transition fitting is used, there is no documentation on how the combination of fittings/parts used will perform, making compliance with Section 300.10 difficult. Using listed transition fittings does provide assurance that the fitting has been tested for a certain purpose and will perform a specified function. This listing provides the AHJ a basis to approve the installation. Using “Homemade” fittings has historically been out of necessity, as there were not listed options available. Now we have several manufacturers that make many different types of listed transition fittings.
ABOUT CQD: The Code Question of the Day (CQD) is NECA and ELECTRICAL CONTRACTOR Magazine’s flagship National Electrical Code (NEC®) public forum for the industry, sponsored by EATON. The daily distribution of Q&A generates a lively dialogue and shares relative Code-based practical responses.
SUBMIT YOUR CODE QUESTION: Click here to submit a question to for inclusion in an upcoming edition of the Code Question of the Day, or email firstname.lastname@example.org.
CHARLIE TROUT: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Even though Charlie passed away in October of 2015, his work continues in spirit. NECA continues to maintain this question forum for its many subscribers in memory and recognition of all his significant contributions to making the NEC what it is today.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. NEIS can be purchased in the NECA Store in three formats: a printed or PDF download of a standard or, as an annual subscription service.
NECA SAFETY PRODUCTS & PUBLICATIONS: NECA produces electrical safety publications and products for the industry including jobsite safety guides, handbooks and resource kits. View a full listing of available resources and products »
IMPORTANT NOTICE: Unless the question requests a response based on a specific edition, all answers are based on the latest edition of NFPA 70® National Electrical Code®.
This correspondence is not a formal interpretation of the NEC® and any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, the NEC Correlating Committee any Code-making panel or other electrical technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
UPDATE YOUR SUBSCRIPTION PREFERENCES: Subscribe or Unsubscribe from this list.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.