Standards as High as Your Own
NECA Online Help Desk Please leave a message
Good morning, Can you please explain the justification behind NEC 210.11(C)(3) including the exception? My understanding is that only one (1) 20-Amp circuit can feed bathroom receptacle outlets. If this is achieved, then the bathroom lighting outlets and exhaust fan can be fed from other circuits. Per the exception, one (1) 20-Amp circuit can feed the bathroom receptacle(s), bathroom light outlets, and exhaust fan as long as this 20-amp circuit only feeds outlets confined to this one (1) bathroom.
I have three (3) bathrooms and one (1) of them is non-compliant with NEC. Within the non-compliant bathroom, the receptacles are GFCI but also feeds: One (1) lighting outlet in the adjacent bathroom One (1) receptacle outlets and one (1) lighting & ceiling fan outlet in the adjacent bedroom Four (4) receptacle outlets and two (1) lighting & ceiling fan outlet in another bedroom. One (1) additional lighting outlet in the associated walk-in closet One (1) lighting outlet in the hallway
In addition, this non-compliant bathroom has an exhaust fan fed from separate circuit that doesn’t have an equipment ground wire connected to the panel. How come only the receptacle outlets are required to be GFCI? Is excess condensation during a hot shower a concern to consider having lighting outlets and exhaust fans within the bathroom be fed from a GFCI breaker? If using the NEC 210.11(C)(3) Exception and feeding all outlets within the same bathroom from one (1) 20-Amp breaker, should a GFCI receptacle outlet be connected first so that all other outlets (lights and fan) will have GFCI protection or on the downstream side of the other outlets (lights and fan)? It seems condensation is not a factor per NEC.
Hey Brandon thanks for your questions, we condensed them slightly to focus on the NEC applications. The need for the 20 ampere branch circuit is based in part on the use of personal grooming appliances. If one (or more) branch circuits supplies bathroom receptacle outlets it must be 20 ampere and can supply no other outlets, such as lighting or exhaust fans as stated in 210.11(C)(3). Even with multiple bathrooms it is not likely that personal grooming appliances will be used in all of them at the same time. And even if that happened the lighting would not be affected as it can't be on that same branch circuit. If a 20 ampere branch circuit is limited to a single bathroom now the lighting and exhaust fan can be supplied from that same branch circuit - if the loads comply with 210.23(A)(1) and (A)(2).
The 15 and 20 ampere 125 volt receptacles installed in dwelling unit bathrooms must be GFCI protected as stated in 210.8(A)(1). This has been based on records of electric shocks and electrocutions related to appliances plugged into these receptacles. Some appliances such as bathroom exhaust fans can include a requirement in the instructions to be GFCI protected and this must be followed as stated in 110.3(B).
In your example several items appear to be non-compliant, especially the lack of an equipment grounding conductor for the exhaust fan. Providing GFCI protection for bathroom lighting is optional unless the luminaire instructions specifically require it.
ABOUT CQD: The Code Question of the Day (CQD) is NECA and ELECTRICAL CONTRACTOR Magazine’s flagship National Electrical Code (NEC®) public forum for the industry, sponsored by EATON. The daily distribution of Q&A generates a lively dialogue and shares relative Code-based practical responses.
SUBMIT YOUR CODE QUESTION: Click here to submit a question to for inclusion in an upcoming edition of the Code Question of the Day, or email firstname.lastname@example.org.
CHARLIE TROUT: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Even though Charlie passed away in October of 2015, his work continues in spirit. NECA continues to maintain this question forum for its many subscribers in memory and recognition of all his significant contributions to making the NEC what it is today.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. NEIS can be purchased in the NECA Store in three formats: a printed or PDF download of a standard or, as an annual subscription service.
NECA SAFETY PRODUCTS & PUBLICATIONS: NECA produces electrical safety publications and products for the industry including jobsite safety guides, handbooks and resource kits. View a full listing of available resources and products »
IMPORTANT NOTICE: Unless the question requests a response based on a specific edition, all answers are based on the latest edition of NFPA 70® National Electrical Code®.
This correspondence is not a formal interpretation of the NEC® and any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, the NEC Correlating Committee any Code-making panel or other electrical technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
UPDATE YOUR SUBSCRIPTION PREFERENCES: Subscribe or Unsubscribe from this list.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.