Standards as High as Your Own
NECA Online Help Desk Please leave a message
Re: Code Question of the Day for May 14 Greetings Code Friends,
My question is if I have a metal outlet box and equipment grounding conductors in the box, do I have to connect the EGC to the box using a listed green grounding screw?
Thanks for participating. No, the connection to the metal box should be made using one of the methods provided in 250.8. If a screw is used to accomplish this connection, it should be in accordance with 250.8(5) and be a machine screw that engages not less than two threads or is secured by a nut. No requirements for such screws to be green or listed. If the connection is made with a grounding clip (pressure connector), the clip would have to be listed.
I think I know why some think that an Equipment Grounding Conductor screw must be required to be listed. I taught electrical wiring in a Vo-Tech High School for 28 years. About 15 years ago there was a textbook that stated the EGC had to be connected to metal boxes with a green listed grounding device or screw. That made it seem that the screw had to be listed and green. The actual wording in the 2002 NEC that the text book was based on said “by means of a grounding screw that shall be used for no other purpose or a listed grounding device.” (250.148(B)). It said nothing about the screw having to be listed or green. The list of permitted methods in today’s 250.8(A) did not appear until 2008. I am sure many of today’s electricians probably were exposed to that book. Before a lot of people write in saying that the screw must engage at least two threads, all 10-32 screws have 32 threads per inch, no matter what color they are or who made them.
Thanks for the comment and additional information. It is a good observation about the language used in the 2002 NEC in Section 250.148(B) that may very well have contributed to the gray area here. The subsequent incorporation of 250.8 has provided the needed clarity.
ABOUT CQD: The Code Question of the Day (CQD) is NECA and ELECTRICAL CONTRACTOR Magazine’s flagship National Electrical Code (NEC®) public forum for the industry, sponsored by EATON. The daily distribution of Q&A generates a lively dialogue and shares relative Code-based practical responses.
SUBMIT YOUR CODE QUESTION: Click here to submit a question to for inclusion in an upcoming edition of the Code Question of the Day, or email firstname.lastname@example.org.
CHARLIE TROUT: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Even though Charlie passed away in October of 2015, his work continues in spirit. NECA continues to maintain this question forum for its many subscribers in memory and recognition of all his significant contributions to making the NEC what it is today.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. NEIS can be purchased in the NECA Store in three formats: a printed or PDF download of a standard or, as an annual subscription service.
NECA SAFETY PRODUCTS & PUBLICATIONS: NECA produces electrical safety publications and products for the industry including jobsite safety guides, handbooks and resource kits. View a full listing of available resources and products »
IMPORTANT NOTICE: Unless the question requests a response based on a specific edition, all answers are based on the latest edition of NFPA 70® National Electrical Code®.
This correspondence is not a formal interpretation of the NEC® and any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, the NEC Correlating Committee any Code-making panel or other electrical technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
UPDATE YOUR SUBSCRIPTION PREFERENCES: Subscribe or Unsubscribe from this list.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.