Standards as High as Your Own
NECA Online Help Desk Please leave a message
Charlie, I have a commercial 120/240V, 1 phase service with two main panels, each with a 200A, 2P main breaker. The panels are located inside the building and are fed directly from the utility meterbase. The owner wants to install an exterior enclosed circuit breaker between the meterbase and each interior panel for maintenance purposes. The two new exterior circuit breakers will now become the service disconnects. There are presently two grounding electrode conductors, the primary one from the metal water service and a secondary attached to a driven ground rod. My question has to do with where to GECs must now connect. They presently are routed to both existing interior panel enclosures. I know the GECs along with the main bonding jumpers will have to be removed from those panels. With the proposed new arrangement, my understanding is that both GECs can land on the neutral bar in the existing meterbase if the local POCO allows. If not, can they be connected to the service neutral in only one of the new exterior circuit breaker enclosures or would they have to be routed to both new enclosures?
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: firstname.lastname@example.org.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.